Title, Curso de vapor Spirax Sarco. Contributor, Spirax Sarco (Firma). Publisher, Spirax Sarco, Length, 84 pages. Export Citation, BiBTeX EndNote. Curso de Vapor por Spirax Sarco, Tuvanosa, Calzada Aeropuerto # Pte Col. Nuevo Bachigualato, Culiacán, Mexico. Mon Oct 17 at. Curso de gestión impartido en Queretaro, gracias por confiar en Spirax Sarco. Expertos en soluciones de energía térmica y vapor. #atodovapor #spiraxsarco.
|Published (Last):||16 May 2014|
|PDF File Size:||5.56 Mb|
|ePub File Size:||18.35 Mb|
|Price:||Free* [*Free Regsitration Required]|
Sizing one is not difficult as they are always sized to match the steam line line size.
As soon as steam has left the boiler, some of it must condense, to replace the heat being lost through the pipe wall. Steam flowing over this film can raise ripples which can build up into waves. It must supply good quality steam at the required rate and at the right pressure.
If this build up continues, the tips of the waves will break off, throwing droplets of condensate into the steam flow. It must do this with the minimum of heat loss, and be economical in capital cost. If taken from the side, or even worse from the bottom, they can carry the condensate from the vpor and in effect become a drain pocket.
The film will also gravitate towards the bottom of the pipe, and so the thickness of the water film will be greatest there. Summarising, we need to consider when selecting our working pressure: Pressure required at point of use Pressure drop along pipe due to resistance of flow friction Pipe spurax losses We also know that steam at a higher pressure occupies less volume per kg.
Enviado por Luiz Felipe flag Denunciar. We must remember however that as the steam passes through the distribution pipework, it will lose some of its pressure due to resistance to flow, and the fact that some of it will condense due to loss of heat from the pipes.
If this build up continues, the tips of the waves.
The result is very wet steam reaching the equipment. This is one location where a correctly sized mechanical drain trap, such as a float trap, can be beneficial.
Insulation will naturally reduce the heat loss, but the heat flow and the condensation rate remain as small but sirax amounts and if appropriate action is not taken these amounts will accumulate. The pressure at which the steam is to be distributed is determined by the splrax of usage on the plant needing the highest pressure.
The condensate will form droplets on the inside of the pipe wall, and these can merge into a film as they are swept along by the steam flow.
Spirax Sarco Chile | First for Steam Solutions
It therefore follows that if we generate steam in the boiler at a much higher pressure than that needed by its application, and we distribute it at this higher pressure the bore of the distribution mains will be smaller for any given mass flow rate. This causes considerable damage to the pipework and ancillaries.
The result is that the heat exchange equipment receives very wet steam. Therefore allowance should be made for this pressure loss when deciding upon the initial distribution fapor.
Catálogo general de productos: Línea Spirax Sarco.
The use of a separator to remove this moisture is shown in the slide. Steam lines are no exception. We already know that dry saturated steam not superheated is to be used for process and heating applications and it is that with which we shall concern ourselves.
Steam leaving a boiler, or other sources, is often much wetter curzo is appreciated and if this water is not removed, there will be poor heat transfer at the point of use this is why the furso needs to be dry.